Time: 2017 Jul 22 4:34:08
Found 2196 logbook entries, displaying most recent 100
Logbook Contents (Most Recent Entries)
21 Jul 2017 Friday 12:31 [Devon] The massive tunnel door has suffered a major failure and is inoperable. Investigation and repair planning is underway, but this will not be a very quick fix. Accelerator and source shut down.
20 Jul 2017 Thursday 15:31 [Justin Warren] I completed Operator 2 training!
17 Jul 2017 Monday 15:31 [Doug Soltesz] Wanted to let everybody know that I completed my operator 2 training. WOOOO!
11 Jul 2017 Tuesday 12:03 [Devon] Replaced the ECO O2 sensors on the VESDA system. Next set due for replacement by 6/20/2019. Order from Orr Protection, not Simplex. Simplex order was at 12 weeks and they couldn't provide any status. Orr order was 3 1/2 weeks.
06 Jul 2017 Thursday 19:51 [Tom Massey] We have completed the measruements for Daren Bleuel from LLNL. Thanks to everyone who has helped in this work. Especial thanks to Don Carter and Devon Jacobs for perservering through all of the problems.
06 Jul 2017 Thursday 16:39 [Tom Massey] I wish to note that we started with a 33 microampere beam of deuterons in the LE cup this morining. This is very goood source performance.
05 Jul 2017 Wednesday 18:27 [Tom Massey] Around 6:15, the sputter source tripped off. The Emergency off button was red, the Dell High voltage and the Glassman high voltages were off. No alarms were sounding. There was lightning from the thunderstorm. A possible cause. Target and Extractor buttons pushed to drop the voltage on startup. Ionizer turned to 10 A. Cs Resivoir and Cs Feed turned off as temperature dropped.
05 Jul 2017 Wednesday 08:09 [Devon] SF6 alarm was sounding this morning. Did a quick leak check before starting the source, tank joint is giving a good hit. Mechanical gauge says we are down 1 psi since last gas transfer. HVAC trouble may be contributing too.
04 Jul 2017 Tuesday 09:59 [Devon] The chiller was factory repaired Monday evening and is functioning normally. Lab systems (except for the 15L chamber) are back to normal and the run can resume as soon as beam comes up Wednesday. The 15L chamber seems to have a pretty good leak somewhere.
03 Jul 2017 Monday 12:59 [Devon] Chiller: Factory service did not show up as advertised today. Unclear why, or when they will, but Wednesday perhaps? Many people on holiday today. The chiller has been running at 50% today, but no guarantee it will stay that way until it is repaired. We continue to keep proccess sytems in a warm water state...
02 Jul 2017 Sunday 09:07 [Devon] The chiller prediction was correct, it shut down. All process chilled pipes dripping with water. Raised all the sub loop temperature settings to get above dew point. Turned off magnets. Analyzer cryo pump seems to have crashed. Valved off and turned off 15L diff pumps since they may not have liked the higher water temps.
01 Jul 2017 Saturday 13:55 [Tom Massey] The emergency crew has done what they can and have called TRANE to be here on Monday. They are unable to clear completely two sensors to allow the unit to run. One is the high pressure cuttoff and the other was the High Pressure in the Coolant Inlet. They have checked the coolant pressures and have made up for any lost coolant. They were unable to connect to the controlling program to reset the system. The chiller has been restarted but is not expected to run long. We will not try to run until Monday.
01 Jul 2017 Saturday 12:39 [Tom Massey] Facilies management has sent three people to work in the Comfort Chiller. The HVAC person in Jeff. The codes read out as high intake pressure. The screens were cleaned, an inline water filter was taken out and cleaned. Make up water was added. They are working on the controls. They are having trouble keeping the chiller running under controls.
01 Jul 2017 Saturday 10:27 [Tom Massey] The comfort chiller has stopped working. The chiller is now warming up. The facilities management emergency number was called and we are waitng for someone to come.
30 Jun 2017 Friday 20:44 [Devon] Darren B. came back from dinner to find the source low flow alarm active. The cause was that the source water pump turned off for some reason, which takes out the source power platform. Nothing else in the building went out. There are reports of a sizeable AEP outage in the area. The pump restatred and continues to run. The source is back on to continue running in the new pellet.
30 Jun 2017 Friday 18:31 [Devon] We changed the source pellet and beam production stalled. Shut down the accelerator and closed gate valves. Letting source run overnight. Beam meter is on 10 uA scale...
29 Jun 2017 Thursday 21:55 [Andrea] The Emergency Off button near the Swinger was pressed while attepting to align the targets in the chamber. This was unintentional and the alarm condition has been reset.
28 Jun 2017 Wednesday 15:58 [Devon] The beam in the swinger became unstable and eventually unusable last evening. The solder link alarm was activating when the swinger cup was operated. Inspection of the swinger cup this morning found that the current lead wire had broken by fatigue. The cup was charging and discharging since it was floating electrically. To compound the issues, the lead wire had a fiberglass insulating jacket on it, and the loose wire and jacket just happened to come to rest on the beam axis blocking beam. Situation has been corrected.
23 Jun 2017 Friday 13:47 [Devon] The beam line is repaired and the leak check was non-detect. We had a bellows section that used to be on the swinger when it had a cryopump. The tubes will need to be monitored and conditioned while going up in voltage next week.
22 Jun 2017 Thursday 15:53 [Devon] There is a vacuum leak in a bellows section of beam pipe at the HE end of the accelerator. The accelerator controls have been disabled and the cryopumps valved off. The leak will vent the tubes to atm overnight for repairs tomorrow.
22 Jun 2017 Thursday 14:47 [Devon] Sputter source cesium reservoir ran dry, bone dry. Glass shards were crystal clear. Feed tube clean. Replaced Cs. Last load was Sept 2016.
15 Jun 2017 Thursday 15:43 [Devon] The police now have access to the restricted area door at the bottom of the main stairs. The police, or the fire department, will only enter the restricted area in certain emergency situations. Otherwise they will wait in the lobby for an operator or keyholder as before. You may see the Standard Operating Procedure (SOP) for when they can and can't enter in the Handbook, Emergency Procedures section. Please read it. There is also a new Emergency Off button by the drinking fountain. It is for them to use if they need to come in and the accelerator is still on with no operator available. You can of course use this button on your way out if something is forcing you to flee the control room.
14 Jun 2017 Wednesday 11:16 [devon] It appears that 120 C is the maximum temperature for producing a carbon beam with the sputter source. Tried 125 and extractor current surged too high.
07 Jun 2017 Wednesday 15:57 [carter] Test message sent to "all operators list" including new operators.
04 Jun 2017 Sunday 06:37 [carter] Modified Tank Volume SF6 hi-res plot on real-time web page to display 32-36 instead of 33-37 bottles SF6.
16 May 2017 Tuesday 13:45 [devon] this is an example
04 May 2017 Thursday 15:20 [carter] The H.E Slit current meter on the Terminal Potential Stabilizer has been replaced. It should not stick on zero anymore. If you notice problems let me know.
29 Apr 2017 Saturday 16:36 [Ingram] Source water was off, so the aplha source power was off. Source water pump restarted. Power restored to the alpha source. All looks good.
29 Apr 2017 Saturday 16:30 [Ingram] There was a power outage this morning that tripped a bunch of alarms that Kristyn reset. Many things did not appear to be affected. But, the pump valve on the HE extension was closed. I reopened it. The valve between the analyzer and switcher magnets was also closed. This valve took a long time to open/operate, about a minute. Also, one filament on the ion gauge is blown. I hope we have a spare, because the next filament failure will require the gauge to be changed.
28 Apr 2017 Friday 11:26 [carter/brandenburg] A concrete density measurement was made by weighing (68.4 Kg, 151 lb.) round concrete core drill slug that came from the control room ceiling. The dimensions were 15.75 in. diameter by 9.5 in. high resulting in a calculated concrete density of 2.33 +- .04 g/cm3. Architectural drawings listed all structural concrete used in the lab construction was 4500 psi compression where concrete used on grade and footers was 3500 psi. This should be the 4500 psi compression concrete.
24 Apr 2017 Monday 15:42 [Devon] The sputter source burned across its extractor insulator. Source has been cleaned. Insulator replaced. Fresh Boron pellet loaded. The existing cesium was preserved under Argon. The "outgassing" procedure will need to be done prior to starting the source. The TV camera is pointed at the source ion gauge vacuum. It can take a long time to get beam from a clean source, don't be afraid to let it run overnight.
17 Apr 2017 Monday 16:15 [Devon] Discovered the cause of the weekend fire alarm in the LTR. The 65R leg gate valve solenoid fried.
16 Apr 2017 Sunday 00:38 [Devon] Fire alarm in LTR pipe 3 (middle bay) and elevated detections on other pipes and control room. Major stink of burned electrical. Emergency lighting CFL bulb in middle of LTR was out, could be culprit. Ran exhaust fans, stink gone, ready for easter bunny.
14 Apr 2017 Friday 11:19 [Alexander] Dear operators, we are going to resume the 11B+48Ca experiment on Monday, April 17, so help with shifts is greatly appreciated. Thanks !
12 Apr 2017 Wednesday 15:53 [carter/jacobs] The HVEC corona current feedthru started leaking SF6 and was also sparking at the designated grid voltage of -10 V. At a grid voltage of -10 volts, the 6BK4C corona current regulator tube plate was 17.5 KV and the corona feedthru was arcing to ground. The original feedthru seemed very fragile and it was decided to replace it with a coaxial cable type compression feedthru that had also been supplied by HVEC for another tank high voltage feedthru and was modified to accept RG-217/U cable and should have a DC breakdown in excess of 50KV. The internal spring/wire spool mechanism was modified to accept the solid core wire of the RG-217/U cable into a receiving socket so that the cable can be replaced without removing the corona point assembly. The short length of cable is inserted into the compression fitting, slides into the center conductor receiving socket and protrudes about 4" outside the tank and terminates into a 5/8" ball spark gap spaced from ground 1.1 cm for a spark gap voltage of approx. 40 KV. A new length of Glassman RG-8/U cable connects at the feedthru spark gap ball and runs to the corona current control module that contains the 6BK4C control tube. There is a spark gap at the plate of the 6BK4C tube inside the NEC corona control unit that consists of two 1/2" brass spheres separated by 1" giving an estimated spark gap breakdown of 80KV. The 6BK4C specifies a max plate voltage of 27 KV. We operate at a nominal corona current of 35uA. The original target grid voltage was -10 volts. At -10 volts on the grid of the 6BK4C the plate voltage was 19.5 KV. At times of instability the control grid could reach -25 volts and the 6BK4C plate voltage would reach 40KV and spark at the original feedthru. A modification was made to the corona control unit to limit the grid voltage to a maximum grid voltage of -15 volts and the 6BK4C plate would be limited to 24.5 KV to protect the tube and the feedthru. Since the stability of the pelletron is very smooth we have modified the standard operating point of the grid voltage to be -5 volts instead of -10 volts. This will lower the nominal voltage at the feedthru from 17.5 KV to 9.2 KV. If more dynamic range of control is needed in the future, the -10V operating point may be safely used at 17.5 KV.
06 Apr 2017 Thursday 13:02 [Devon] The active shooter training (ALiCE) will be offered on both Tuesdays, 4/11 & 4/18, from 9:00-12:00. The first 2 hours will be the general ALiCE training that could help you at anytime and anyplace in this day and age. The third hour will be to discuss the unique hazards that could arise in the accelerator lab. I have to admit, during the planning meeting for this training, a lot of good, useful, suggestions came up. This is not a mandatory training and its not just for operators and keyholders, tell your associates in the building too.
04 Apr 2017 Tuesday 13:04 [Devon] As requested, trying to set up active shooter training for everyone. Possible dates are Tuesday, 4/11, 9:00-12:00, or Tuesday, 4/18, same time. More info to follow...
31 Mar 2017 Friday 11:09 [carter] Dr. Andreas Ruben of W-IE-NE-R Plein & Baus Corp will be in the R.W Finlay Conference Room at the Edwards Accelerator Lab on Monday 3 April 2017 at 10:00 AM to demonstrate new equipment offerings they have for nuclear data acquisition and control needs. See http://www.wiener-us.com for info on their products. Please spread the word to anyone you feel might benefit from the demonstration.
28 Mar 2017 Tuesday 14:08 [Devon] The high voltage feedthru on the corona probe is failing. As a precaution the SF6 in the accelerator is being taken down to 0 psig (1 atm) to prevent gas loss. This means that we are extremely limited in capabilities until we are ready to make a permanent repair. It is our hope that we can still support the lab class for RBS, but there will be special operational parameters. You can read more about the saga in the logbook.
28 Mar 2017 Tuesday 14:02 [Devon] There was a spark after 2 hours of operation. The grid was running at -5 which corresponds to 10 KV at the corona feedthrough. Normal operation would give 18 KV at the feedthrough. We measured current and voltage on the corona feedthrough and found the values to be as expected, however the feedthrough continued to spark as soon as we reached 15 KV. Then we discovered that the feedthrough is also leaking SF6. The leak pegged both ranges on the new detector and still registered on the less sensitive old detector. Taking the gas down to 1 atm to prevent loss by catastrophic failure.
27 Mar 2017 Monday 15:45 [Devon] We’ve had a spell of spark trouble. Trying to run at 4 MV and repeated sparks. Reached the point that sparks were happening at 3.4 MV. But no sign in the data of resistor noise, charging system working fine, all indications that everything is normal. Began testing. Retracted the corona points and ran quite nicely at 4.1 MV. Moved the corona points in to operating distance started controlling – spark. Tried again, spark without controlling. Moved points back out, everything fine. Put a grounded current meter directly on the corona feedthrough to eliminate tube and HV cable, everything fine while passing 35 uA of current. Found the Teflon (?) insulator that was around the feedthrough had a spark hole in it. Shortened the Teflon insulator so that burn spot was not at the HV point, drilled out the burned spot too. Put everything back and spark. Changed the HV cable and tube, spark again. Cleaned the feedthrough and removed the Teflon (?) insulator and it all seems to be working at 4.017 MV. Experiment resuming…
22 Mar 2017 Wednesday 18:29 [Alexander] Dear operators We are starting a new experiment with the 11B 20 MeV beam on 48Ca target. This is collaborative experimet with faculty and students from Central Michigan University. They will come on Friday, March 24 and we will be running from Friday, March 24 to Friday March 31. I would like to ask students to help with shifts (including weekend March 25-26, if possible) and also encourage students to come and talk to visitors and see what is going on. Thank you.
16 Feb 2017 Thursday 09:15 [carter] Surveyed small target room and could locate no failed equipment. Tested DAQ systems and module electronics and all seem OK. Campus closed for water main break.
16 Feb 2017 Thursday 03:30 [Devon] There was a fire alarm that originated in the small target room at 02:28. There was also minor detections in Vault pipe 1. FD and PD were waiting when I arrived. On inspection, there was a distinct smell of burned electrical compents in the STR but smoke levels were back to normal. Unable to identify the source of the burn. Mech and Diff pumps still working, lights all working. Need to be on the lookout for for failed electrical component....
02 Feb 2017 Thursday 13:01 [Devon] I have scheduled fire alarm testing for Monday, 2/6, at 8:00 am.
30 Jan 2017 Monday 11:02 [Alexander] Fisrt of all, many thanks to Kristyn Brandenburg, Andrea Richard and Rekam Giri for their great help with shifts last week, and would like to remind operators that we are running this week as well and still need to fill in 3 evening shifts on Tuesday, Wednesday and Friday (01/31, 02/01, and 02/03/2017). Thank you !
27 Jan 2017 Friday 17:16 [carter] A new Epson PowerLite 955WH LCD Projector has been installed in the R.W.Finlay conference room. It is brighter, better resolution and has more inputs (HDMI also). Please give it a try before attempting to give a presentation and get familiar with it. The new HDMI cable is labeled "overhead HDMI 1". Other input cables are the same as before.
20 Jan 2017 Friday 10:51 [carter,massey,brooks] Radiation monitor yearly calibration check, each detector at 10, 20, 40 mR OK. 80% alarm check OK and 100% machine shutdown OK.
20 Jan 2017 Friday 10:09 [Alexander] We are going to start a new run on Monday, January 23, with a deuteron 0.5 MeV beam on Tritium target. This will be a continuation of the experiment on the deuteron break up cross section measurements in support of experiments at the National Ignition Facility of Lawrence Livermore Lab. We will try to keep it running for two weeks, so help from operators is needed. You are welcome to join the experiment by signing up for shifts , help on evening shifts is more preferable but other time slots are also welcomed. Thanks !
19 Jan 2017 Thursday 15:34 [Devon] Tank Opening, December 2016. --- 4419 chain hours. --- Searching for source of instability in GVM, tube/column downcharges, and tube entrance lens. Suspicious of gas quality and recirculation effectiveness. --- Inspected LE Tube grid entrance lens, nothing remarkable. Cleaned both LE Penning gauges. --- New blower to recirculate SF6. Old blower had much wear, would have taken more shop time than the cost of a new one. Also new pressure relief valve for blower, set for 6 psi. Old PRV was worn and chattered when running, filled pig with brass flakes. Source of noisy recirculator for how many years? New blower is producing 4 psi head, therefore PRV not opening in normal use. Very quiet. New chain coupling also. --- Corona points replaced. Current set from last entry had worn points with mild deposits. Replaced with tungsten points. 0.13" protrusion. 0.0125 - 0.1563 is range. --- Added selector valves and a pressure transducer to each of the 3 filter canisters in the recirculation loop. Replaced filters. Tried to seal filter cans with 4401 thermoseal gasket material but small leaks were present. Seal surfaces not smoothly machined. Switched to viton gaskets. Pressure drop data as follows: Blower in/out: 4.1 psi, Tank in/out: 1.2 psi, Dryer/Scrubber: 1.9psi, V1 Filter: 0.3 psi, V19 Filter: 0.3 psi, Dryer Filter: 0.3 psi. --- Changed Scrubber sieve material. All 3 sieves gained weight. 5A 11%, 4A 6%, 3A 9%. --- Inspected all resistors, all good. --- In the end it turned out that the GVM grounding brush was the problem, see separate notes on that.
19 Jan 2017 Thursday 13:36 [carter] Radiation monitor vault detector zero unstable. This amplifier was the last remaining original Kiethley K302 electrometer amplifier. It has now been replaced with a Burr Brown OPA128 electrometer amplifier as the others have been replaced.
17 Jan 2017 Tuesday 17:57 [carter] The GVM assembly was removed and upon disassembly it was found that the shaft grounding brush had broken off of the spring clip and was causing the resistance from the shaft to ground to fluctuate from 10 - 80 ohms measures with an ohmmeter, probably conducting through the bearings. The carbon brush was epoxied back onto the spring clip using silver bearing conductive epoxy. After repair the resistance from shaft to ground was a very stable 0.7 ohm (lead resistance).
17 Jan 2017 Tuesday 17:51 [carter] GVM electronics was tested using an SRS DS345 function generator and gave very good results. The DS345 was set to output a symetric triangle wave at 531 HZ and injected at the leads that connect to the gvm, signal lead connected through a 0.0175 uF capacitor and the shield lead to shield wire. GVM meter at console reads about 1.061 MV for a function generator output of 0.1 volts. Voltage read on console was extremely stable, +-1 KV.
04 Jan 2017 Wednesday 10:27 [Devon] Pelletron hour meter reading 1/1/2017: 4419. Accelerator operating hours in 2016: 1144.
15 Dec 2016 Thursday 09:55 [Devon] EPS was here for quarterly testing of the security system and looked at the cell phone issues during generator tests. Found cell battery wired backwards. Replaced it. Then generator guys showed up for test. No security system trouble. Problem solved.
08 Dec 2016 Thursday 13:55 [carter] Realtime accelerator logging will be down for upgrade. Hopefully back up by quitting time.
16 Nov 2016 Wednesday 09:50 [carter] The accelerator lab firewall has been upgraded to a new computer running the most recent release of Endian Community Firewall 3.2.1. If you experience any firewall related issues, please let me know. don
14 Nov 2016 Monday 08:56 [Devon] The alpha source diff pump heater has failed. Don't know if its heater or wiring issue yet. Na heater, He gas, and high vac gauge shut off. Will pursue after sputter source run.
06 Nov 2016 Sunday 21:04 [Alexander] We are going to continue the experiment started in January 2016 with Oslo-MSU-MCU collaboration. This time we will measure 68Zn(7Li,p)74Ge reaction to study the level density of 74Ge. The run will start on Monday and is expected to be continued this and the following week. Operator help would be appreciated. The sign up sheet is on the door of the control room. Students-operators, if interested, are welcome to learn more about the experiment and physics by talking to me, Steven Grimes and/or Magne Guttormsen - Oslo University professor who will be visiting us on November 10-11. Thanks !
14 Oct 2016 Friday 16:25 [carter] Test of all operators email...
14 Oct 2016 Friday 16:24 [carter] Test of logbook send message to Zach Meisel... Zach, Please let me know firstname.lastname@example.org if you get this test message. don
10 Oct 2016 Monday 10:42 [carter] Firewall power supply failed. New Antec VP450 installed.
07 Oct 2016 Friday 09:41 [Devon] Cleaned the coils on the process chiller this week. Big improvement in performance.
06 Oct 2016 Thursday 16:56 [carter] Ran today after recirculating gas overnight. No column current instabilities were seen like were seen yesterday but also did not attempt to go above 4.0 MV. Ran at terminal 1.7, 2.48, 3.45 and 3.98 MV.
05 Oct 2016 Wednesday 18:06 [carter] Ran at 1.7 MV and column and tube currents seemed about normal again after the problems seen at higher terminal voltages.
05 Oct 2016 Wednesday 16:24 [carter] In the run at 8 MeV (term = 3.957 MV), after about 30 minutes of running the vertical column current had slowly risen to about twice its normal value. When I noticed it, the current sum plot showed approximately zero but I noticed the column current and the high energy current were the same. The sum indicated zero because the up-charge had been increased to compensate for the additional current down the vertical column. I ran the terminal down to 0.5 MV to check the current ratios there. The vertical column dropped below the HE tube current but didn't return to its proper value, still a little high. I have turned the terminal down to 0 up-charge, self charge was .020 MV.
05 Oct 2016 Wednesday 15:13 [carter] 2 machine sparks today trying to reach 4.5 MV. First at about 4.3 MV shortly after a sharp 17 uA rise in vertical column current. No instability in LE vacuum preceded the spark. LE tube was conditioning normally with no rise in vacuum. About 2 hours later a second attempt to reach 4.5 MV also caused a spark at about 4.2 MV and was also preceded shortly with an increase in vertical column current of about 18 uA. Decided to run at 8 MeV (term = 3.957 MV) for the MIT high energy run. Maybe need to try drying gas before going above 4 MeV?
27 Sep 2016 Tuesday 19:56 [Alexander] Cs reservoir temperature dropped again (along with a beam current) replicating the behaviour seen in prevouse runs with a deuteron beam (see entries below).
27 Sep 2016 Tuesday 09:18 [Alexander] Need help with shifts, from Tuesday to Friday, September 27-30. 0.5 MeV deuterons on tritium target to produce 15 MeV neutron beam which will bombard heavy water to study deuteron break-up cross section. Thanks.
20 Sep 2016 Tuesday 14:39 [carter] Sputter source target supply was turning off after about 30 minutes running at about 5 KV and 6.5 mA. Supply would stay off about 10 minutes then turn back on. Cause was bad cooling fan in the supply. The cooling fans in both the Target amd Extractor supplies were replaced. Both had been in operation for 21 years, since 1995.
20 Sep 2016 Tuesday 09:03 [Devon] VESDA O2 detectors calibrated today. Next calibration due 3/20/17. Sensor manufacture date is 5/7/2015, they will need replaced next May or so, 2 year life.
12 Sep 2016 Monday 12:25 [Devon] Cs sputter source cesium reservoir had run dry. The last charge was 2 Sept 2015. The reservoir has been re-charged. The reservoir heater was checked out with a power supply and seemed to work fine. The source will be checked out with protons tomorrow.
10 Sep 2016 Saturday 13:19 [Tom Massey] Increasing the resivoir current did not increase the temperature. Don suggested there may be a short. We turned the current down to avoid further damage to the heater.
09 Sep 2016 Friday 13:53 [Tom Massey] The current has been falling around the same time every day during this run. In checking for a possible cause, the cesium resevoir temperature was found to drop over 10 degrees near the time as the reduction in the beam. We have increased the Cs heater current to 0.270 from 0.260 amp to offset this drop in temperature.
09 Sep 2016 Friday 09:14 [Don Carter] Don Carter has received tritium safety certification.
09 Sep 2016 Friday 09:13 [Jeremy Browne] I am now Tritium Certified!
08 Sep 2016 Thursday 09:19 [Kristyn Brandenburg] I have received tritium safety certification.
07 Sep 2016 Wednesday 17:33 [Alexander Voinov] I have received tritium safety certification.
07 Sep 2016 Wednesday 16:48 [David Ingram] I have received tritium safety certification.
07 Sep 2016 Wednesday 16:24 [Carl Brune] I have received tritium certification.
07 Sep 2016 Wednesday 16:14 [Nadyah Alanazi] I have received a tritium safety certification.
07 Sep 2016 Wednesday 10:00 [Rekam Giri] I have received a tritium certification.
07 Sep 2016 Wednesday 09:32 [Tyler Danley] I have received a tritium safety certification.
07 Sep 2016 Wednesday 09:32 [Som Nath Paneru] I have received a tritium safety certification.
07 Sep 2016 Wednesday 09:31 [Andrea Richard] I have received a tritium safety certification.
07 Sep 2016 Wednesday 08:53 [Thomas N. Massey] All operators who wish to participate in the current run with a solid tritium target should see me for training. The training on the standard operating procedures for running with a tritium target is required before you can run shifts with tritium
06 Sep 2016 Tuesday 12:05 [Alexander] We started D(n,2n) experiment I would like to call for operators. Please sign up downstairs if you can. We are running through this week until Saturday. Evening slots are available. However, if you want to take day shifts, just cross my name and put yours. Thank you.
31 Aug 2016 Wednesday 14:42 [Tyler Danley] I am now Operator 2!
30 Aug 2016 Tuesday 15:26 [Jeremy Browne] I am officially operator 2!
29 Aug 2016 Monday 16:10 [Kristyn Brandenburg] I am now an operator 2!
24 Aug 2016 Wednesday 13:52 [Som Nath Paneru] I am certified operator 2 for Edwards Accelerator facility. Thanks to evryone.
22 Aug 2016 Monday 16:22 [Colton Feathers] I am now officially Operator 2 certified!
05 Aug 2016 Friday 15:53 [jacobs] Tank opening, August 2016, 4095 hours. The terminal generator drive belt broke in two places, leading to upcharge being cut in half for expected suppressor/inductor voltages. Also found two floating vacuum planes (broken springs) near the exit end of the HE tube. Some disassembly required at the upper chain sheave to install a new drive belt: 1) Remove both electrodes and the carbon brush arm from their T shaped mounting block, hex head bolts. 2) remove the T shaped mounting block from the sheave base plate, two recessed allen head bolts. 3) raise and block the drive motor cradle to remove chain tension. 4) Pass new generator belt between chain and sheave. 5) Loosen generator tension bolt, install belt, re-tension, re-assemble.
03 Aug 2016 Wednesday 12:01 [jacobs/carter] We've had our first unplanned Pelletron charging system failure. It seems that we have lost the suppression/induction power supplies in the terminal as the upcharge is suddenly half of what we would expect. This loss of exactly half would indicate that both upper supplies failed, or, the AC generator failed, or, the AC generator drive belt failed. We'll hope for drive belt. Gas out Thursday morning....
19 Jul 2016 Tuesday 09:11 [Devon] Something fried in the HVAC air compressor starter box. FM electricians will come back tomorrow, when we're not running, for repairs.
14 Jul 2016 Thursday 17:31 [DCI] Ludlum DRD returned today at 3:00 PM by Crystal following their rcalibration check. She took the back the loaners.
14 Jul 2016 Thursday 06:24 [DCI] I have started the alpha source. David
13 Jul 2016 Wednesday 14:11 [carter] Test of mail to all operators after adding "Browne, Jeremy"
08 Jul 2016 Friday 10:29 [carter] Analyzing magnet would not run down. Seemed like an intermittent mechanical connection, when I attempted to slide the control chassis out I could hear it immediately run down and start working again. In an attempt to locate a possible intermittent, I have tightened all screws on the connection barrier strips, re-seated the variac servo drive transistors in their sockets, checked for any loose component leads on the circuit board and also cycled the auto/manual servo mode switch several times.
07 Jul 2016 Thursday 08:39 [DCI] Yesterday Grass cut should be back to treat large weeds near edge of the roof. A contractor walked through the building looking for places to put hot and cold water meter. I told him we had an ineffective water heater now. Mike West and Todd Schram(sp?) looked at the flashing on the roof damaged by a mower. Mike will get with Facilities about repairing it. He said they may use the contractor doing the Clippinger roof. We had a meeting with them today, that was why he and Todd were around. I also reminded him about the problmes with the undercapacity downspouts.